For use to seal openings, gaps, joints and gussets in fire protection systems.
The Tangit FP 450 fire protection compound can also be used in accordance with the MLAR model wiring system guideline of 10.02.2015 to close openings in room-enclosing building components (walls and ceilings) through which the following cables are routed:
Electrical cables, e.g. power cables, telephone cables, EDP cables, fibre optic cables.
Combustible pipelines, e.g. PB, PE, PVC, composite pipes as well as empty pipes for electrical lines up to a maximum outer pipe diameter of 32 mm.
Non-combustible pipelines, e.g. copper, steel and cast iron up to a maximum outer pipe diameter of 160 mm.
Compound foaming in case of fire (intumescence)
Complies with DIN 4102-B1 and MLAR ("Musterleitunmgsanlagenrichtlinie").
Provides a minimum of 90 minutes fire protection.
Fast and easy application.
Free of plasticizers, solvents and halogens.
Expansion factor in case of fire 7 13
Air permeability: no air passage up to pressure difference 600 Pa
VOC emission class A+ (Decree France 2011-321)
Compound foaming in case of fire (intumescence) for the fireproof sealing of electrical cables, telecommunications cables and optical fiber cables.
The substrate must be clean and dust-free.
Completely fill the cavities between the cable strands with Tangit FP 450 in the entire wall thickness